In the new home decoration, general bathroom design basically with convenient, safe, easy to clean and decent appearance, but because the toilet water is very heavy, security has become the most attention level, although we all know that you want to use good quality wire and switch socket, but for our choice and installation of socket and switch are not very clear.
Selection of switches and sockets
Taking into account the bathroom was a place where people living in the water up to the toilet, the switch socket must choose to buy some good quality brand waterproof switch and socket, prevent people from danger in the shower and other water. In order to prevent children from electric shock, with finger touch or metal objects inserted into the hole of the power supply, we must choose the safety socket with safety block, that is, the industry called "shielded socket". The author recommends the use of electric water heater users, in order to ensure absolute safety, must be waterproof three sockets use good quality, grounding protection can not let down hole; the use of Yuba warm up support in the bathroom outside the entrance of the installation of a double switch, a control room lamp, a control of Yuba, which can guarantee the beautiful and easy to use, but also to ensure the safe use of electricity.
Installation of switches and sockets
Switch socket installation is best, please have experienced electrician master, but we should also know some installation knowledge. Here are some of the installation points, we can see.
1 、 switch installation
The concealed switch requires the distance from the ground 1.2m-1.4m and the horizontal distance from the doorframe 150mm-200mm. The position of the switch shall be in accordance with the position of the lamp, and the switch height in the same room shall be identical.
2 socket installation
Two single eye socket wiring requirements are: when perforation horizontal configuration for the "left zero right vertical arrangement for fire", "lit by zero": three single eye socket wiring requirements are: the most grounded perforations must line up with grounded prison, and then on, can not then, the remaining two perforations on the "left zero right fire" wiring rules, it is worth noting that the zero line and the protective grounding wire must not be wrong then or now as a whole.
In addition, some use in the bathroom appliances, can switch outside the best, if not, must pay attention to the waterproof switch, socket, switch and socket and the best to stay away from the bathing area, the height of not less than 0.5m on the ground, lest the bathroom water escapes into the accident.